**Power System Stability, Swing Equation, Power Output of the Generator, Equal Area Criterion, Application of Equal Area Criterion, Expression for critical clearing angle δ**

_{CC.}**Power System Stability**

A power system at a given operating state is stable if following a given disturbance or a set of disturbances. The system stays within specified bounds and the system reaches a new stable equilibrium state within a specified period of time.

The stability studies which evaluate the impact of disturbances on the behavior of synchronous machines of the power system are of two types:** transient stability and steady state stability.**

- The
**transient stability**studies involve the determination of whether or not synchronism is maintained after the machine has been subjected to a severe disturbance. This may be a sudden application of large load, a loss of generation, a loss of large load, or a fault (short circuit) on the system. In most disturbances, oscillations are such magnitude that linearization is not permissible and nonlinear equations must be solved to determine the stability of the system. - The
**steady-state stability**is concerned with the system subjected to small disturbances wherein the stability analysis could be done using the linearized version of nonlinear equations. In this experiment, we are concerned with the transient stability of power systems.

In practice, load change may not be gradual. Further, there may be sudden

disturbances due to

- Sudden change of load
- Switching operation
- Loss of generation
- Fault

**Swing Equation**

Where *M* = *I*ω = Angular momentum in J-s mechanical radian.

* I* = Moment of Inertia.

* P _{a}* =

*I*αω =

*T*ω = Accelerating power

_{a}α = Angular acceleration

ω = Angular velocity

* P _{s}* = Shaft power

* P _{e}* = Electrical power

δ = Power angle or torque angle

**Inertia Constant**

Inertia constant

Stored energy in megajoule = *G × H*

**Inertia constant (H) on a Common Base**

Where S = MVA rating

**Key Points**

- The equivalent inertia constant (
*H*) of several identical machines working in parallel is the same as that of any one of the machines (_{eq}*H*)._{eq}= H - The equivalent inertia constant (
*H*) of two machines on a common base swing coherently_{eq}*H*_{eq}= H_{1 }+ H_{2} - The equivalent inertia constant (
*H*) of two synchronous machines which do not swing together is._{eq}

**Power Output of the Generator**

Consider the following figure, for the calculation of power flow

Complex power output of the generator

Where, *E* = | *E *| < δ = Voltage behind direct axis synchronous reachtance of generator

| *V* | = Terminal voltage of generator

*X _{d}* = Direct axis synchronous reactance of synchronous machine

Active power output of generator

Reactive power output of generator,

Where

*P _{t}* = Synchronizing power coefficient

**Power Flow**

For lossless line *R* = 0 and the transmitted power.

*R* *+ jX* = z<θ

For lossless line, *R* = 0 and the transmitted power.

Where *V _{s}* = Sending end voltage

*V _{R}* = Receiving end voltage

*X* = Reactance of the line

δ = Load angle

**Key Points**

- For maximum power transferring δ = 90
^{o}

- For power to be maximum

**Equal Area Criterion**

The accelerating power in swing equation will have sine term. Therefore the swing equation is a non-linear differential equation and obtaining its solution is not simple. For two machine system and one machine connected to infinite **m** bus bar, it is possible to say whether a system has transient stability or not, without solving the swing equation. Such criteria which decide the stability makes use of the equal area in power angle diagram and hence it is known as **EQUAL AREA CRITERION**. Thus the principle by which stability under transient conditions is determined without solving the swing equation, but makes use of areas in power angle diagram, is called the EQUAL AREA CRITERION.

In a two-machine system, under the usual assumptions of constant input, and constant voltage behind transient reactance, the angle between the machines either increases indefinitely or else, after all, disturbances have occurred, oscillates with constant amplitude. In other words, the two machines either fall out of step on the first swing or never. Under these conditions, the observation that the machines come to rest with respect to each other may be taken as the proof that the system is stable. There is a simple graphical method of determining whether the machines come to rest with respect to each other. This method is known as the equal area criterion of stability.

When the fault occurs at t=0, the electrical power output is suddenly zero while p_{m} is unaltered. The difference in power must be accounted for by a rate of change of store kinetic energy in the rotor masses. This is accomplished only by an increase in speed which results from the constant accelerating power p_{m}.

After reaching δ_{2, }δ(t) will oscillate until losses and the load damp oscillations and δ(t) = δ_{0}

If δ_{2} > δ_{3} the generator loses stability because of p_{e} < p_{m} and the generator continue to accelerate.

**Sudden load increase on Synchronous motor**

Let us consider a synchronous motor connected to an infinite bus bar.

The following changes occur when the load is increased suddenly.

Point **a Initial condition**; Input = output =** P _{o}**; ω = ω

_{s}; δ= δ

_{o}

Due to sudden loading,

**output = Ps**;

**output > Input**;

ω decreases from ω

_{s}; δ increases from δ

_{o}.

**Between a-b Output > Input**

Deceleration; ω decreases; δ increases.

Point b Output = Input; **ω=ω _{min}** which is less than

**ω**;

_{s}**δ = δ**

_{s}.Since

**ω**is less than

**ω**, continues to increase.

_{s}**Between b-c Input > output**

Rotating masses start gaining energy;

Acceleration; **ω** starts increasing from minimum value but still less than **ω _{s}**; continues to increase.

**Point c; Input > Output**

** ω= ω _{s}; δ= δ_{m}**; There is acceleration; ω is going to increase from ω

_{s}; hence δ is going to decrease from δm.

**Between b-a Output > input**

Deceleration; ω starts decreasing from ω_{max} ;

but still greater than ωs; δ continues to decrease.

**Point-a;** **ω= ω _{s}; δ= δ_{0}**; Output > Input; The cycle repeats.

Because of damping present in the system, subsequent oscillations become smaller and smaller and finally b will be the steady state operating point.

**Interpretation of equal area**

Thus for stability, area **δ _{0} a b c δ_{m}** = area

**δ**

_{0}a d e δ_{m}Subtracting area

**δ**from both sides of above equation, we get

_{0}a b c δ_{m}**A**. Thus for stability,

_{2}=A_{1}

**Below we are showing for three different cases:**

The one shown in **case a** is **STABLE**. **Case b** indicates **CRITICALLY STABLE** while **case c** falls under **UNSTABLE.**

** Application of Equal Area Criterion**

**Opening of one of the parallel lines**

When a generator is supplying power to an infinite bus over two parallel transmission lines, the opening of one of the lines will result in an increase in the equivalent reactance and hence decrease in the maximum power transferred. Because of this, depending upon the initial operating power, the generator may lose synchronism even though the load could be supplied over the remaining line under steady state condition.

**Short circuit occurring in the system**

Short circuit occurring in the system often causes loss of stability even though the fault may be removed by isolating it from the rest of the system in a relatively short time. A three-phase fault at one end of a double circuit line is shown in Figure below which can be reduced as shown in next figure.

It is to be noted that all the current from the generator flows through the fault and this current **Ig** lags the generator voltage by **90 ^{o}**. Thus the real power output of the generator is zero. Normally the input power to the generator remains unaltered. Therefore, if the fault is sustained, the load angle will increase indefinitely because all the input power will be used for acceleration, resulting in unstable condition.

When the three-phase fault occurring at one end of a double circuit line is disconnected by opening the circuit breakers at both ends of the faulted line, power is again transmitted. If the fault is cleared before the rotor angle reaches a particular value, the system will remain stable.

**Expression for critical clearing angle δ**_{CC}

_{CC}

## Comments

write a commentArchana MamidiNov 27, 2016

Anurag KumarDec 1, 2016

Def UvwFeb 19, 2017

This comment is hidden because it was marked spam.

NikkyDec 18, 2017

Raj MangalOct 1, 2018

KrishnaSep 14, 2019