# Study Notes on System Stability Concepts For Electrical Engineering Students

By Yash Bansal|Updated : May 23rd, 2021

In this article, you will find the study notes on System Stability Concepts which will cover the topics such as Power System Stability, Swing Equation,  Power Output of the Generator, Equal Area  Criterion, Application of Equal Area Criterion, Expression for critical clearing angle δCC.

In this article, you will find the study notes on System Stability Concepts which will cover the topics such as Power System Stability, Swing Equation,  Power Output of the Generator, Equal Area  Criterion, Application of Equal Area Criterion, Expression for critical clearing angle δCC.
Power System Stability

A power system at a given operating state is stable if following a given disturbance or a set of disturbances. The system stays within specified bounds and the system reaches a new stable equilibrium state within a specified period of time.

The stability studies which evaluate the impact of disturbances on the behavior of synchronous machines of the power system are of two types: transient stability and steady state stability.

• The transient stability studies involve the determination of whether or not synchronism is maintained after the machine has been subjected to a severe disturbance. This may be a sudden application of large load, a loss of generation, a loss of large load, or a fault (short circuit) on the system. In most disturbances, oscillations are such magnitude that linearization is not permissible and nonlinear equations must be solved to determine the stability of the system.
• The steady-state stability is concerned with the system subjected to small disturbances wherein the stability analysis could be done using the linearized version of nonlinear equations. In this experiment, we are concerned with the transient stability of power systems.

In practice, load change may not be gradual. Further, there may be sudden
disturbances due to

• Switching operation
• Loss of generation
• Fault

Swing Equation Where M = Iω = Angular momentum in J-s mechanical radian.

I = Moment of Inertia.

Pa = Iαω = Taω = Accelerating power

α = Angular acceleration

ω = Angular velocity

Ps = Shaft power

Pe = Electrical power

δ = Power angle or torque angle

Inertia Constant

Inertia constant Stored energy in megajoule = G × H Inertia constant (H) on a Common Base Where S = MVA rating

Key Points

• The equivalent inertia constant (Heq) of several identical machines working in parallel is the same as that of any one of the machines (Heq = H).
• The equivalent inertia constant (Heq) of two machines on a common base swing coherently Heq = H1 + H2
• The equivalent inertia constant (Heq) of two synchronous machines which do not swing together is. Power Output of the Generator

Consider the following figure, for the calculation of power flow Complex power output of the generator Where, E = | E | < δ = Voltage behind direct axis synchronous reachtance of generator

| V | = Terminal voltage of generator

Xd = Direct axis synchronous reactance of synchronous machine

Active power output of generator Reactive power output of generator, Where Pt = Synchronizing power coefficient

Power Flow

For lossless line R = 0 and the transmitted power. R + jX = z<θ

For lossless line, R = 0 and the transmitted power. Where Vs = Sending end voltage

VR = Receiving end voltage

X = Reactance of the line

Key Points

• For maximum power transferring δ = 90o • For power to be maximum ### Equal Area Criterion

The accelerating power in swing equation will have sine term. Therefore the swing equation is a non-linear differential equation and obtaining its solution is not simple. For two machine system and one machine connected to infinite m bus bar, it is possible to say whether a system has transient stability or not, without solving the swing equation. Such criteria which decide the stability makes use of the equal area in power angle diagram and hence it is known as EQUAL AREA CRITERION. Thus the principle by which stability under transient conditions is determined without solving the swing equation, but makes use of areas in power angle diagram, is called the EQUAL AREA CRITERION. In a two-machine system, under the usual assumptions of constant input, and constant voltage behind transient reactance, the angle between the machines either increases indefinitely or else, after all, disturbances have occurred, oscillates with constant amplitude. In other words, the two machines either fall out of step on the first swing or never. Under these conditions, the observation that the machines come to rest with respect to each other may be taken as the proof that the system is stable. There is a simple graphical method of determining whether the machines come to rest with respect to each other. This method is known as the equal area criterion of stability. When the fault occurs at t=0, the electrical power output is suddenly zero while pm is unaltered. The difference in power must be accounted for by a rate of change of store kinetic energy in the rotor masses. This is accomplished only by an increase in speed which results from the constant accelerating power pm.

After reaching δ2, δ(t) will oscillate until losses and the load damp oscillations and δ(t) = δ0

If δ2 > δ3 the generator loses stability because of pe < pm and the generator continue to accelerate.

Sudden load increase on Synchronous motor

Let us consider a synchronous motor connected to an infinite bus bar. The following changes occur when the load is increased suddenly.
Point a Initial condition; Input = output = Po; ω = ωs; δ= δo

ω decreases from ωs; δ increases from δo. Between a-b Output > Input

Deceleration; ω decreases; δ increases.
Point b Output = Input; ω=ωmin which is less than ωsδ = δs.
Since ω is less than ωs, continues to increase.
Between b-c Input > output

Rotating masses start gaining energy;
Acceleration; ω starts increasing from minimum value but still less than ωs; continues to increase.
Point c; Input > Output

ω= ωs; δ= δm; There is acceleration; ω is going to increase from ωs; hence δ is going to decrease from δm. Between b-a Output > input

Deceleration; ω starts decreasing from ωmax ;
but still greater than ωs; δ continues to decrease.

Point-a; ω= ωs; δ= δ0; Output > Input; The cycle repeats.

Because of damping present in the system, subsequent oscillations become smaller and smaller and finally b will be the steady state operating point.

Interpretation of equal area  Thus for stability, area δ0 a b c δm = area δ0 a d e δm
Subtracting area δ0 a b c δm from both sides of above equation, we get A2=A1. Thus for stability,

### Below we are showing for three different cases:

The one shown in case a is STABLE. Case b indicates CRITICALLY STABLE while case c falls under UNSTABLE. ### Application of Equal Area Criterion

• Opening of one of the parallel lines

When a generator is supplying power to an infinite bus over two parallel transmission lines, the opening of one of the lines will result in an increase in the equivalent reactance and hence decrease in the maximum power transferred. Because of this, depending upon the initial operating power, the generator may lose synchronism even though the load could be supplied over the remaining line under steady state condition. • Short circuit occurring in the system

Short circuit occurring in the system often causes loss of stability even though the fault may be removed by isolating it from the rest of the system in a relatively short time. A three-phase fault at one end of a double circuit line is shown in Figure below which can be reduced as shown in next figure. It is to be noted that all the current from the generator flows through the fault and this current Ig lags the generator voltage by 90o. Thus the real power output of the generator is zero. Normally the input power to the generator remains unaltered. Therefore, if the fault is sustained, the load angle will increase indefinitely because all the input power will be used for acceleration, resulting in unstable condition.

When the three-phase fault occurring at one end of a double circuit line is disconnected by opening the circuit breakers at both ends of the faulted line, power is again transmitted. If the fault is cleared before the rotor angle reaches a particular value, the system will remain stable. Stable, critically stable and unstable conditions of such systems are shown in figure below  ### Expression for critical clearing angle δCC   Thus CRITICAL CLEARING ANGLE is given by  Here the angles are in radian. Further, since  Pm1sinδ0 = Ps  & δm = π- δs, angles δ0 and δm are given by If you are preparing for GATE and ESE, avail GRADEUP SUPER to get unlimited access to all the live structured courses and mock tests from the following link :

• ## ESE and GATE EE SUPER (24+ Live classes and 193+ mock tests)

Thank you,

Shai Prep hai to Life Set Hai !! Member since Nov 2018 GradeStack Learning Pvt. Ltd.Windsor IT Park, Tower - A, 2nd Floor, Sector 125, Noida, Uttar Pradesh 201303 [email protected]